US $155.00 / piece
|Battery type and serial number||LFP(16S)||NCM(14S)|
|Continuously charging/discharging current||50A||100A||150A||200A||50A||100A||150A||200A|
|Communication protocol||CANBUS(defult) RS485(Please contact Sale man)|
|Custom function||Heating function,External switch,RS485 protocol|
|Discharge Output Impedance||<2mΩ|
|Current Balance||Passive balance||150mA(Max)|
|Power consumption||Working mode power consumption||<40mA|
|Sleeping mode power consumption||0uA|
|Capacity protection||Nominal capacity||5-500Ah|
|Remaining capacity protection||5%|
|Short Circuit protection||Short circuit protection lock||Continuously short in the output circuit|
|Short circuit protection lock times||5 times|
|Short circuit protection lock release||Connected with charger|
|Individual cell voltage protection||Over voltage protection||3650mV||4200mV|
|Under voltage protection||2700mV||2900mV|
|Voltage protection||Over voltage protection||57.6V||58V|
|Under voltage protection||41.6V||40.6V|
|Current protection||Over current protection||60A||110A||160A||210A||60A||110A||160A||210A|
|Over current protection||30mS|
Technology upgrade :
The BMS can add module now,check below for detail:
|Bluetooth modules||USD 10|
|Heating modules||USD 10|
|Heating pad||USD 60|
With Bluetooth modules,user can manage the battery on the phone conveniently;
and with heating modules,user can make sure there is heat enough to run the battery Systems when temperature below 0 ℃ or even below -20℃.
Temperature: environment temperature, temperature of cells and BMS PCB.
State of charge: indicate the charge level of the battery.
Current: current in or out of the battery.
CANBUS 24/48V 8S/16S 200A lithium iron phosphate battery smart monitoring management system 1
Our BMS can support up to 16 units in parallel operation.
RS485 communication(RS485 can be customize)
Under voltage protection
Charge, discharge and ambient temperature protection
Charge and discharge over current protection
Charge current limitation
Short circuit protection
CANBUS communication method:
Now our CANBUS communication board supports these brands of inverters,and our BMS has built-in CANBUS protocol of matching inverter brand, which can be automatically matched or manually switched:
The default is the Pylontech CANBUS protocol
Growatt(The default is SPF(off-grid) protocol. If your inverter is SPH(on-grid) , please contact the sales person)
PS:If the inverter brand not in the listed,please ask your inverter supplier for the protocol define.And sent it to us,we 'll help confirm that
RS485 communication method
Now our RS485 communication board supports these brands of inverters,The BMS with RS485 communication has a built-in RS485 protocol, please confirm with the salesman before buying what you need is that one RS485 protocol:
The default is the Pylontech RS485 protocol
PS:If the inverter brand not in the listed,please ask your inverter supplier for the protocol define.And sent it ti us,we'll help confirm that.
Q: Can the 485 version and CAN version of the V14 BMS change the baud rate of the BMS by refreshing the program？
A: NO, they are different version of the chip.
Q: Is it an equalizing function, active or passive and what is the equalizing current?
A:It’s a passive equalizing function with 150mA current.
Q: What is the connection mode of communication when BMS communicates with inverter or 485 communication and CAN communication?
A: External communication means that BMS is connected to CANBUS interface when communicating with inverter (RS485 interface is used for communication with Voltonic inverter)
Q: The BMS cannot work and indicator does not light up.
A: May be caused by D4 diode damage.
Q: Which BMS model suitable for ternary lithium battery?
A:The ternary lithium battery can support up to 14S version of the BMS. The firmware version of the ternary lithium battery BMS is different from the lithium iron phosphate BMS and cannot be used universally.
Q: SMA and Victron inverter will report fault when BMS is fully charged.
A: The fault can be solved by refreshing the firmware program (version 2.8). The V16 BMS does not have this fault.
Q: Voltronic inverter and its licensed inverter only have 485 communication version of BMS or new version of BMS (V16 version). How to use the inverter?
A: The Voltonic inverter uses RS485 interface for communication. DIP dialing is different from other versions of BMS. Connect and dial 1on to the host, 2on to the first slave, and 3on to the second slave. You can ask me to send relevant documents.
Q: How is BMS function of SOC calculating and cycle life counting work?
A: First, modify the rated capacity of the battery, then complete a full charge and discharge process,the actual battery capacity will be learned.SOC is calculated by capacity accumulation and voltage calibration.
It has the function of calculating the number of charging and discharging cycles. When the cumulative discharge capacity of the battery pack reaches the set full capacity.At 20% (default), the number of cycles increases one,the set value of battery cycle capacity parameter can be changed through the upper computer.
Q: The issue of battery monitoring software cannot see the master when multiple BMS are in parallel.
A:When multiple BMS are in parallel, the battery monitoring software cannot see the information of the master, only see the information of the slave. If you want to see the information of the master, you need to turn off the DIP of the master and connect it separately or use the LCD screen with Bluetooth function, or use the onboard BMS with Bluetooth function.
Q: Why not message display on LCD screen?
A: 1.The function of LCD did not open.
2.Poor contact of connecting or broken wire of LCD screen.
3.The new version BMS with Bluetooth, but install with an LCD screen without Bluetooth.
Q:limited algorithm of charge current.
A:Unbalanced in current distributed.
1.no charge current if any device is in charging warning of voltage,temperature,and capacity or charging protection.
2.charge current values remain in 10.0A when no device in charging.
3.charge current is base the role if over current is greater than 20.0A then reduce 10.0A,otherwise,remain in 10.0A when single device is charging.
4.charge current is base the role of over current value multiply by device’s quantity then divide by two if more than two device is charging.
5.charge current will be cleared and set the chargeable value to 0A when any single cell voltage more than +30mV compare to over voltage protection value with battery pack in parallel.
Q:what if customer want to purchase BMS but the inverter in use is not in compatible list.
A:Customer need to provide the communication protocol of their inverter.
Q:Battery monitoring software not working or load protocol failure.
A:1.Download new program.2.set the correct format language(as below)
Q:The functions of heating and heating pad choosing.
A:BMS with heating function need to customized because the heating pad size is not specific,customer need to purchased by themself and current can not over 4A.
Q:The specification of 12V BMS in series or in parallel.
A:In series or in parallel is available but only individually,4 BMS is limited in series but no limit in parallel.
Q:About firmware program upgrade.
A:Not allow to upgrade the Firmware program without permission,after sales service is not available if its cause any damage.
Q:The temperature shows at -50℃
A:NTC temperature sensor damaged or welding disengaged.
Q:The conditions to use one key to power on/off.
A:Master BMS can control slave one to power on or off when battery working in parallel.it could not be one key to power on/off if master address is not dial(the new version BMS can be dial automatically) and all BMS is not in standby mode(because current of the battery will flow each other if there is not in standby mode when in parallel).
Q:Is it the BMS can change to another model to use by load the parameter?
A:NO(such as 13S and 14S,15S and 16S can be changed by load the parameter,but this will not recommended because it could be lead to malfunction)
Q:Running normal but there is busbar over voltage warming.
A:Please check if battery circuit connection is correct.
Q:Is there any other way can know the status of BMS?
A:1.browse on PC software.2.check the message on LCD screen.3.check the status of LED in BMS(as description of manual)